I am converting a Intermatic Timer to a Multiwave and have a question about the wiring. I am add a GFI CB to power terminal 5 which powers switch 3(Terminal 6) and 4 (Terminal 7). I plan to terminate the coiled breaker neutral to the neutral bus. The hot from breaker to terminal 5. The hot from one light to terminal 6 and the hot for the other light to terminal 7. I know that the neutral goes back to the neutral connection on the breaker (GFI). Is it ok to pigtail the two neutrals from the two lights to the breaker, and are both lights GFI protected?
27.8 KB Views: 4