I had some issues with improper bonding work done by my electrician. They tell me that they have rectified all issues and passed the electrical inspection (the inspector didn't come out but they sent pictures to him). I just noticed that my bonding wire is connected to my pump with a zip tie and I'm wondering if this looks acceptable, or if my electrician messed up again. Thank you for any advice!
638.8 KB Views: 51