Ground-Fault Circuit Interrupters (GFCI)
The Ground Fault Circuit Interrupter continuously monitors the the difference in current between the hot and neutral conductors. If the electricity going to a circuit is equal to the current back from the circuit the GFCI is dormant. If the electricity going to a circuit is greater than 5ma then the current coming back, the GFCI will open the circuit and stop the flow of electricity.
The purpose of the GFCI is to prevent severe electrical shocks. Ground faults occur when the electrical current in an circuit strays outside its normal path, and the human body becomes part of the path through which the electrical current may flow.
National Electrical Code Requirements
The National Electrical Code covers pool requirements in Section 680. The NEC is revised every 3 years and pool requirements have evolved. Below lists the current code requirements:
- Pool motors require GFCI protection whenever they’re rated 120V, 208V, 240V, 15A or 20A (added in 2008)
- All electrical outlets must be at least 6 feet from the inside of the wall and must be GFCI protected. (changed in 2017)
- GFCI protection is required for ALL 15-amp, 20-amp, 125V, or single phase electrical outlets installed within 20 feet from a pool
- GFCI protection is required for ALL receptacles that supply power to the pool equipment, such as water heaters and pump motors.
- GFCI Protection is required for ALL underwater lighting operating over the low-voltage contact limit
- GFCI Protection is required for ALL light switches
The GFCI breakers called "personnel protection" are the ones required by code. "Personnel" protection breakers should not trip at less than 4 milliamps and should trip at 6 milliamps or higher. "Equipment protection" GFCI circuit breakers that trip at 30 milliamps should not be used around pools or spas.
GFCI Circuit Breakers
How it Works
The circuit breaker gfci works similarly to a clamp ammeter. For example, if you had L1, L2 and Neutral and you put a 240 volt, 10 amp load on the system, L1 and L2 would each carry 10 amps.
If you measure L1 or L2, you should read 10 amps on each leg. However, if you clamp over both lines at the same time, the current would read zero because the current's magnetic field in the forward direction cancels the current's magnetic field in the reverse direction.
If you then added a 120 volt, 5 amp load, you would measure 15 amps on one hot leg, 10 amps on the other hot leg and 5 amps on the neutral.
A clamp ammeter around any 2 or 3 wires will measure the net difference between current in both directions.
Putting the meter around all 3 wires should cancel and read zero amps.
As long as the neutral goes through the breaker, the total current in both directions should cancel.
So, a breaker doesn't really measure current and compare to make sure that the current is the same. It works on a cancelling effect.
As long as the current in both directions cancels, the breaker won't trip.
GFCI 20A CB for VS Pumps
Harmonics from the variable frequency drive can cause false GFCI trips. Pentair PA220GF is a 20A 240V GFCI breaker that GFCI trips at 6ma. The PA220GF is supposed to be less sensitive to false GCFI trips from VS pumps.
The PA220GF is a relabeled Siemens CB (QF220AP) although some say Pentair may have additional quality control and selects breakers less susceptible to false GFCI trips.
The The National Electrical Safety Foundations (NESF) and vendors suggest homeowners test their ground fault circuit interrupters (GFCI) every month - especially during thunderstorm season.
Each GFCI circuit breaker or receptacle has a built-in test button to test the device. It is very important to test each and every GFCI in your home once a month. To test a GFCI circuit breaker, make sure the breaker handle is in the "ON" position. Depress the "TEST" button. This will cause the handle to move to an intermediate "tripped" position indicating that the GFCI is functioning properly. Reset your circuit breaker by pushing the handle to the "OFF" position first, then "ON." If the circuit breaker fails to trip, it must be replaced.
- GFCI breakers are doing their job when they trip when sensing a small imbalance. This type of small current imbalance is less then what would trip a regular circuit breaker.
- Moisture from rain or sprinklers can cause a GFCI to trip
- Some breakers are less sensitive to electrical noise from transformers, variable speed pumps, and lighting controls. Siemens breakers are recommended by some pool equipment manufacturers to be the least sensitive to false GFCI trips.
- Keep your pump dry and not sitting in a puddle or area of excess runoff to prevent GFCI trips.
Mixing of CB Manufacturers in Panels
Financially, it makes sense for manufacturers to specify their own breakers for use in their panel boards and not list competitors’ products; even though they too are suitable for use. This is why a third party organization (Underwriters Laboratories Inc.) is responsible for listing suitable replacements for the manufacturer’s specified circuit breakers. Our classified circuit breakers meet all code acceptance regulations governed by the National Electric Code® and Underwriters Laboratories Inc.
Original Panelboard Warranty
Original panelboard manufacturers may claim that the use of breakers other than those specified voids their warranty. However, the Magnusson-Moss Warranty- Act prevents manufacturers from making warranties contingent upon the use of their replacement parts, as long as the third-party part is safe. Since the safety has been proven by UL, the panelboard manufacturer’s warranty is still effective when you choose a CL or CHQ breaker.