wow. so how do you bond it? its there kit to buy? also, if your pump was plugged into a GFCI outlet, and something shorted out that would cause an issue like electrified water, similar to that in the video, i would think it would trip the GFCI shutting power to pump off, and eliminating this issue. So wouldnt a GFCI outlet be enough?
Bonding is primarily an issue with inground and metal AG pools. It consists of connecting all of the metal parts of and near the pool and the water itself together electrically.
A GFCI won't necessarily help because the source of the electricity may be unrelated to the pool or your property. For example, a construction crew using a backhoe that contacts an overhead line could energize the ground and the current might flow through your pool.