Oh then this might be a good option! Tristar no additional warranty used @ $600, or the VS with one year warranty (or two year for additional $39) @ $700.00 OTDFor the TriStar SP3210EE, I get the following operating point
122 GPM @ 36' of head
Return Head = 27.7'
Suction Head = 8.4'
Head ratio = 3:1
The suction head loss is low enough and head ratio is high enough where cavitation should not be an issue.