Long time lurker, first time poster.
I am installing an Easytouch 8.
I have a single pool light.
I have a GFCI circuit breaker in the Easytouch exclusively for the pool light.
I want the Easytouch to control the pool light.
Do I wire both the hot and neutral from the GFCI circuit breaker to the relay or just the hot?
Typically you do not switch the neutral, ever, even with a relay.
The reason I am asking is because of this post from wayback, answer #19. I just want to make sure I understand this answer.
Thanks, great forum, great website!!!