Thought I better confirm something before I proceed. I just installed a new Intelliflo VF which is 220v (replaced a Whisperflow 220v). I am also upgrading to a new gfci 2 pole breaker. I know the green ground runs from the pump to the ground bus bar in the Easytouch. The two load wires from the pump run to the two load terminals on the new gfic breaker. The white pigtail running from the gfic then is connected to the neutral bar. My question is since there no (white) neutral wire from the pump, then the load neutral terminal on the gfic breaker is not used. Does that sound correct? If so, will this breaker still "trip" if it senses as it's supposed to?
I have the exact same setup for the Minimax 400 heater, so I will be duplicating the same wiring to it's own individual gfic breaker.
This is the gfic: Siemens QF220 Circuit Breaker 20A 2P 120/240V 10K QPF GFCI 5MA