Moving along, ready to hand the EasyTouch panel. I'm supplying 50 amps from the garage panel to the ET Sub-panel using 6awg. It's a short run, about 2 feet (more wire will be in the boxes than out). Is there a particular size conduit I'm required by code to use? I'm in Virginia.